The Veris AC Kilowatt Transducer incorporates three split-core AC current sensors and three voltage leads and outputs a signal proportional to kilowatts of power (demand). Accepting an input primary voltage of 480 Volts AC rms, this transducer requires a Pulse Input Adapter. Because these sensors tie directly into the line, they should be used only by qualified personnel. NOTE: Not recommended for use with variable frequency drives.
- Split-core installation eliminates the need to remove conductors
- Self-contained 0 to 800 AMP current transducer for large 3-phase AC loads
- Accurate electronic pulse output
In what environment does this sensor operate?
This sensor operates in an indoor environment.
What measurements does this sensor support?
The T-VER-8053-800 sensor supports the following measurement: Kilowatt Hours (kWh)
Frequency: 50 to 60Hz
Accuracy: ±1% (3-phase model conforms to ANSI C12.1 metering standards)
CT range: 0-300 Amp (T-VER-8051-300); 0-800 Amp (T-VER-8053-800)
Circuit connection: 3- or 4-wire
Maximum output current: 100mA at 24VAC/DC
Operating temp range: 0° to 60°C (32° to 140°F)
Operating humidity range: 0-95% RH (non-condensing)
Output signal to HOBO Energy Logger: Pulse (Normally open Opto-FET)
Pulse width: 200 msec
Opening dimensions of each CT
T-VER-8051-300: 3.8 x 3.2 cm (1.5 x 1.25"?)
T-VER-8053-800: 7.3 x 6.2 cm (2.9 x 2.5"?)
Number of data channels: 1
To download the manual from Veris click here.